F2-T

The F2-T is a 50V, two zone smoke detector controller used for conventional circuits, as you operate the controls of the console and it will send the signal to the main fire alarm control panel (FACP) for its 2 zonal circuits e.g pressing the "Silence Sounders" button will deactivate sounders, pressing the "Reset" will reset these zones etc., which will send the signals back to the FACP such as the F4 or F16e, or via a loop responder on the addressable loop of the F220, F120A or F100A.

Product Overview
The Pertronic F2-T is a 50V operated, two zone, automatic fire alarm control panel with two conventional detection zones.

The F2-T operates from a 50 Volt (nominal) dc power supply. It can be configured to operate from a 24 Volt (nominal) dc power supply.

Features

 * Single or dual mode operation of detector circuits
 * Smoke detectors, heat detectors, and manual call points may be installed together on the same circuit
 * Front panel and internal bell cut off
 * Internal isolate switch
 * Off normal door interlock
 * Detector and manual call point circuit self test
 * Fire and defect relay contacts
 * Front panel reset push-button
 * Supervised bell circuit for external sounders
 * Built-in piezo alarm
 * Operates from 50 Volt (nominal) dc power supply, configurable to operate from 24 Volt dc (nominal) dc supply