FR1

Pertronic's newest product the FH1/FR1, is a compact Fire Alarm Control Panel designed primarily for domestic use. The Fire Alarm system comprises the following components, connected to the Pertronic FH1/FR1:


 * fire detection components : smoke or heat detectors, manual call-points
 * integrated or separate visual and/or audible alerting devices o a 2-wire system supports the detectors, MCP’s and Alerting devices on the same circuit
 * optional sprinkler connection.

The FR1 can also be used as an end of line device to control a zone on conventional circuits of the F1, F4, F16e, a loop responder, an apartment module or a System Sensor intelligent monitor module on an analogue addressable loop.

More info about this product see: https://pertronic.co.nz/products/panels-networking-and-software/fire-alarm-control-panels/conventional-panels//product/40

Product Overview
The Pertronic Residential Fire Panel (FH1, FR1) is a cost effective, easy to use single zone, two-wire fire alarm system for the residential housing market. The panel provides a fault-supervised fire detection and sounder zone over a single two-wire connection.

This simple to install unit is housed either in a dual gang flush box or in a surface mount enclosure.

The facia has an intuitive user interface with clear operating instructions. A front-panel Hush facility silences the sounders for 2 minutes, to allow occupants to deal with nuisance alarm issues such as smoke from cooking.

An onboard rechargeable battery provides 48 hour standby in case of mains failure.

The Residential Fire Panel supports the System Sensor 2WTA-B combined heat and smoke detector with built-in sounder. The panel is also compatible with Pertronic manual call points and heat detectors; together with System Sensor 100-series conventional detectors, and conventional alarm devices.

Built-in Fire, Defect and Test relays allow interfacing with other equipment.

Features

 * Two-wire single zone combined detection and alarm system with full defect supervision
 * Up to 10 System Sensor 2WTA-B combination heat & smoke detectors with built-in alarm sounders
 * Sprinkler input with defect supervision
 * Mains-powered
 * Protected charging connection for 12 V 1.2 Ah gelcell battery (not included)
 * 48 hour mains failure stand-by period, when fitted with recommended battery
 * Intuitive front panel user interface
 * Hush function
 * Automatically resets detectors at the end of the Hush period
 * Flush or surface-mount versions
 * Fire, defect and test changeover relays
 * Earth defect monitoring
 * Compatible with standard PDL dual flush cover
 * Supplied with Surface Mount or Flush Mount back box