F100A

The F100A is an addressable panel designed for general applications in places where they need most e.g community facilities, industrial warehouses etc.. It is very similar to the F120A.

More info about this product see: https://pertronic.co.nz/products/panels-networking-and-software/fire-alarm-control-panels/analogue-addressable-panels//product/2

Product Overview
The F100A analogue addressable panel is a fire alarm control panel (FACP) for installations that require flexible configuration and control functions.

The F100A complies with New Zealand Standard NZS 4512:2010 and with the requirements of the New Zealand Building Code.

Seismically Tested: Independent testing by an IANZ-accredited laboratory has verified that the Pertronic F100A meets the requirements of NZS 1170.5, the NZ standard for earthquake loading. The test used an earthquake simulation based on International Standard ICC-ES AC-156, Acceptance Criteria for Seismic Certification by Shake-Table Testing of Nonstructural Components.

Features

 * Precise Identification of Fire Location with user-definable English language text description
 * Large 2 x 40 character back-lit LCD Display
 * 24-character configurable text message per Address, Zone, Logic Block, Timer and Network input
 * Automatic ‘Pre-Alarm’ warnings
 * Automatic 24-Hour ‘System Test’ of all Detectors and Battery
 * 2 to 4 Loops provides a maximum 396 detectors plus 396 modules or manual call points (MCPs)
 * Supports 127 nodes on the Pertronic network
 * Supports up to 64 outputs to the network and 64 inputs from the network
 * Loop input devices include detectors, call-points, loop responders, loop relays, and modules
 * Addressable loop relays can be configured as Sounder relays, Auxiliary relays or Door Holder relays, etc
 * User Isolation of zones and individual detectors
 * 2560 Event Historical Log
 * Configuration data may be entered through the front panel controls or using PC Configuration Utility
 * Optional seismic battery bracket SBB-17AH
 * Independently tested and verified by an IANZ-accredited laboratory as compliant with NZS 1170.5, the NZ standard for earthquake loading