Fire Tracker

Brooks Australia Pty Ltd. have a range of fire detection and alarm control and indicating equipment called "Fire Tracker". Fire Tracker panels made by Brooks, come in both standard conventional and intelligent varieties.

When safety is paramount, it is important to choose a market leader in fire equipment and solutions.
FireTracker Conventional Panels are ideal for all commercial, industrial and residential applications.

Overview
The Brooks FireTracker Conventional CIE, FT420, is a highly integrated, highly configurable and flexible Fire Alarm Control Panel. It has been designed and manufactured to comply with AS7240.2 and AS7240.4 standards. It has been tested and approved under the CSIRO ActivFire scheme. The product with correct configuration and installation is suited to a wide range of applications which require reliable detection, occupant warnings and ancillary control.


 * Simple and clear user interface – the CIE modular and intuitive user interface significantly simplifies the system operations. It provides users with all the necessary information and controls at a glance via the individually well-grouped indicators and momentary push-button switches.
 * Audible and visual indications – it is capable of providing visual and audible warning for fire alarm evacuation conditions using external strobe output and warning output. If an OWS option is added, the FT420 system provides additional fire safety by using both alert and evacuation tones and messages.
 * Less disturbance during tests – if OWS is used, the CIE broadcasts clear and brief voice messages to the specified speakers during the alarm tests and walk test “Testing”. It ensures the efficiency of the system routine tests and minimises unwanted disturbances to occupants.
 * Gaseous extinguishing system – the FT420 can incorporate a Brooks dual stage gaseous extinguishing system that meets the relevant clauses of the Australian Standard AS4214.
 * Brooks AlertCom – custom programming converts the FT420 CIE into a fully functional Occupant Management System enabling the tailoring of 8 unique tones to prompt a specific response.   All tones can be activated manually and via automatic triggering.

Features
The Brooks FireTracker FT420 consists of the following components:


 * Configurable for 4 to 20 Conventional Zones
 * Individual Zone Controls & Status Indication
 * Supervised Alarm Devices output and Disable facility
 * Supervised Ancillary Control Facility (ACF), independent control and indication
 * Supervised External Strobe output and Disable facility
 * Walk Test facility
 * Occupant Warning System
 * Multiple programmable supervised speaker circuits (optional)
 * Multiple programmable supervised 24V outputs (optional)
 * Multiple programmable clean contact outputs (optional)
 * AlertCom i.e. multiple tones / messages manual and automatic triggering
 * Gaseous dual stage extinguishing system control module (optional)

Brooks knowledge and expertise ensure you receive the most effective solution for your business.
Our range of FireTracker intelligent analogue addressable fire detection and alarm systems are suitable for a variety of installations.

Overview
Quality, reliability, flexibility and maintainability are necessary elements of today’s fire alarm systems. Brooks FireTracker Analogue Addressable Control and Indicating Equipment (CIE), detectors and loop devices provide this and more, allowing system designers the ability to produce a cost effective, functionality correct and compliant alarm system for a wide range of building applications.

Our addressable systems meet the most stringent requirements in order to secure real fire alarms and to reduce nuisance alarms.

Fire Alarm Control Panels - FDCIE
Brooks FireTracker intelligent analogue addressable panels (FDCIE), conform to Australian Standards, AS7240.2 Control and Indicating Equipment, AS7240.4 Power Supply and AS4428.3 - 2010 Fire Brigade Panel standards. Panels are available as a standalone 1 loop (FT128) or networked capable 4 loop (FT1020G3) option. Each loop capable of communicating with up to 255 devices.

Optional Features

 * 8 Way Conventional Input Module
 * 8 Way Programmable Relay Module
 * Remote Display Units
 * Zone Control Module
 * AS1668 Fan Controls
 * Generic Switch and Indicator Module
 * Occupant warning system
 * 1598 Webserver supports for High Level Interface, Nurse Call Interface, Remote Monitoring and High Level Graphical Interface
 * Gaseous dual stage extinguishing system control module (optional)

Protect your assets with a state-of-the-art gas suppression system.
Monitor and control your gas extinguishing system.

Overview
The Brooks FireTracker FT2GAS is an Extinguishing Control Panel with all the features required for a wide variety of coordinated suppression release applications. The FT2GAS is based around the FT2-FP, 2 zone conventional CIE with the addition of a plug in gas control module, designed to comply with the Detection, Actuation and Control Systems section of AS4214 2002 Gaseous Fire Extinguishing Systems.

Features

 * Intelligent dual microprocessor system which combines both the two zone CIE functions and the dual zone gas control functions
 * Built-in dual power sources
 * System maximum current capacity is 5A @ 27.5V DC
 * Adjustable gas release timer 0.2 – 90 seconds
 * System functionality configuration via DIP switches
 * All outputs for the simple connection of fully compatible local control station, warning signs, strobes and sounders
 * Optional web server interface for Ethernet connectivity with web pages and email alerts
 * Designed to meet the requirements of AS7240.2 and AS7240.4 and relevant clauses of AS4214 standards. The FT2GAS (which includes FT2FP) has been independently assessed and certified by CSIRO to these standards